Emergency Power Control
Chase Nipple Mounted
The SENSORWORX Emergency Power Control device provides a simple method of converting standard light fixtures into emergency light fixtures for a UL924 compliant emergency application. The SWX-EPC-A-2 family ensures compliance with both life safety and energy codes and eliminates the wasted energy that is used when emergency lighting is kept on 24 hours a day. These devices have both ears and a chase nipple, allowing them to be mounted in a variety of places as needed.
All lighting fixtures (both normal and emergency) are controlled on and off (and/or dimmed) together during normal power operation by common lighting control devices (i.e. switches, dimmers, occupancy sensors, daylight harvesting photocells, relay panels, etc.). However, during a utility power interruption, the SWX-EPC-A-2 will automatically bypasses the controls and override to on all the fixtures designated for emergency operation. With the dimming option, the unit can also ensure that controlled emergency lighting is returned to its full bright level.
The SWX-EPC-A-2 family also has a patented automatic diagnostic feature. When a room’s switch is turned off, the SWX-EPC-A-2 will run a 2.5 second self-test routine, verifying that the emergency power source is available and that the unit and connected fixtures are all functioning correctly. This feature eliminates the need for time-consuming and costly manual monthly testing and is approved for this purpose. This also allows the unit to be installed in remote or inaccessible locations, because the diagnostic feature does not rely on access to its manual test switch.
Features / Emergency Power Control
Patented Automatic Diagnostics
Mounting via ears or a 1/2 chase nipple
Easy Front Access to Manual Test Switch
Integrates with Fire Alarm Systems for Override
Remote Test Configuration
Utility Power Indicator LEDs
0-10V & DALI Dimming Option
2.15”H x 1.63”W x 1.38”D without ears/nipple
(5.46 x 4.14 x 3.51 cm)
Surface Mounts Using Ears
Suitable for Installation in Plenum
Green: Utility Power Present
MANUAL TEST BUTTON
16A @ 120-277VAC
LED DRIVER/ELECTRONIC BALLAST LOAD:
16A @ 120-277VAC
5A @ 120-277VAC
1800W @ 120VAC
3000W @ 277VAC
0-10 VDC ballasts or drivers compliant with IEC 60929 Annex E.2
32°F to 140°F (0°C to 60°C)
Single Line Drawing
Basic Wiring Diagrams
MODEL #: SWX-EPC-A-2 (Standard Configuration)
A common switch controls both normal and emergency lighting in a space. Upon loss of normal power, the emergency lighting comes on regardless of switch position.
MODEL #: SWX-EPC-A-2 (Shunt Configuration)
A dedicated switch controls emergency lighting in a space. Upon loss of normal power, the emergency lighting comes on regardless of switch position.
MODEL #: SWX-EPC-A-2-D
A common dimmer controls both normal and emergency lighting in a space. Upon loss of normal power, the emergency lighting comes on to full bright regardless of dimmer position.
FIRE ALARM / REMOTE TEST SWITCH WIRING
The unit’s red low voltage jumper wire is an override input to connect in a fire alarm or remote test switch. For more information visit http://www.lvscontrols.com/assets/UL924FAI.pdf.
Wiring with Sensorworx Controls
EXAMPLE 1: WIRING WITH LOW VOLTAGE SENSORS & POWER PACK
EXAMPLE 2: WIRING WITH LOW VOLTAGE SENSOR, POWER PACK, & DIMMER
EXAMPLE 3: WIRING WITH DIMMING WALL SWITCH SENSOR
EXAMPLE 4: WIRING WITH WIRELESS POWER PACK
EXAMPLE MODEL # SWX-EPC-A-2-D
|SWX-EPC-A-2||Emergency Power Control - Ears/Chase Nipple Mount|
|SWX-EPC-A-2-D||Emergency Power Control w/ Dimming - Ears/Chase Nipple Mount|