Wireless Fixture Controller
w/ 0-10V Dimming
SENSORWORX wireless fixture controllers switch on/off power to a connected lighting fixture as directed by wirelessly linked sensors, photocells, and wall controls. Additionally, the unit’s 0-10V dimming output simplifies applications where dimming control is required.
The SENSORWORX wireless fixture controller is intended to switch and dim a single lighting fixture. It utilizes a powerful microprocessor to optimize its switching timing, ensuring long relay life even when controlling high-inrush LED lighting. As with all SENSORWORX products, these controllers are easy to install and incorporate features that reduce contractor labor time. An elongated chase nipple with snaps for quick installation makes for a hassle-free contractor experience. All SENSORWORX products are proudly made in the USA.
A received wireless message indicating occupancy from one or more wirelessly linked sensors will trigger the controller’s integrated relay to close. When configured for Vacancy operation, an ON switch message is required from a wirelessly linked wall station to initially trigger lights. Once closed, line voltage will flow through the relay and turn on the connected lighting load. The wireless fixture controller maintains a master time delay that is reset every time a linked sensor reports occupancy. Lights will be switched off once there hasn’t been an occupancy message reported for the duration of the time delay. If linked to a photocell, the unit receives light level readings and controls connected lighting according to its photocell operating mode.
Individual Fixture Level Control In Spaces Such As:
Features / Wireless Fixture Controller
Wirelessly Links to Sensors, Photocells, & Wall Stations
Links in Seconds up to 50 Remote Devices
Intended to Switch a Single Lighting Fixture (1A maximum)
Electronically Timed Switching (i.e. Zero Crossing) Ensures Long Relay Life
Integrated Test/Programming Button
0-10V Dimming Output for Partial On & Partial Off Operation
Configurable Time Delays and Operational Modes (e.g. Occupancy/ Vacancy)
Configurable Daylight Harvesting & Photocell Modes
Configurable Dimming Trim Levels & Fades Rates
Plenum Rated (UL 2043)
3.00” H x 2.25” W x 1.88” D
(7.62 cm x 5.72 cm x 4.78 cm)
TEST / PROGRAMING BUTTON
LED STATUS INDICATOR
Bi-color White & Blue
Occupancy & Vacancy
TIME DELAY OPTIONS
1, 5, 10, 15, 20, 30 min
32°F to 122°F
(0°C to 50°C)
Indoor Use Only
80’ line of sight w/o obstruction
40’ with obstruction (walls/floors)
915 MHz ISM Band
Simple 3 sec. Push Button Process
All Wireless Data is Encrypted
These power packs can be used to
meet ASHRAE 90.1, IECC, & Title 24
energy code requirements
Single Phase, 50/60 Hz
1A @ 120-277 VAC switching max
No more than 3 drivers or ballast
Relays use zero-cross switching
6 mA, of 0-10 VDC ballasts or drivers
(compliant with IEC 60929 Annex E.2)
Tested to withstand electrostatic discharge
without damage or memory loss
Wireless Linking (Pairing)
Linking a wireless fixture controller to a wireless sensor, photocell, or remote wall station is quickly done via the following procedure:
Step 1. Enter learn (pairing) mode by holding down the controller’s button for 3 seconds until the LED starts alternating white then blue, then release.
Step 2. At the sensor, photocell, or remote wall station, hold down the programming button for 3 seconds until the LED starts alternating white then blue. Releasing will link the device with the wireless fixture controller in learn mode (see note 1 below). The lighting load being controlled will also be toggled off/on as a visual indication of success.
Step 3. Repeat step 2 to link additional devices.
Step 4. When all devices have been linked, exit learn mode on the fixture controller by pressing the button 1 time. Learn mode will also be automatically closed after 15 minutes of no new devices being linked.
Note 1: When in learn mode, the alternating LED colors on the fixture controller will periodically pause and blink out the total number of linked devices. There will be no blinks during the pause until the first device is linked.
EXAMPLE MODEL # SWX-951-D1
|SWX–||Power Pack||951–D1||Wireless Fixture Controller, 1A @ 120-277 VAC with 0-10V Dimming Output|
Compatible Wireless Products
Wireless Dimmer & Switch
These stylish and intuitive wall stations are designed for a 10 year battery life.
Wireless Ceiling Sensors
Available with either PIR and Dual Tech. occupancy detection, these wireless sensors can be paired with a load controller in seconds.
Wireless Wide View Sensors
With five contractor friendly mounting methods, locating a sensor in a corner has never been easier.