Photocell & Daylight Harvesting
Line Voltage – Fixture Mount
The SENSORWORX fixture mounted photocell and daylight harvesting sensor is a convenient self-contained control solution. Basic on/off units are capable of directly switching lights off when ambient levels are high enough that desired overall light levels will be still be maintained. Lights will be switched back on once ambient level falls below the desired setpoint.
Units with the daylight harvesting (dimming) option track a space’s overall illumination and dim connected lighting to achieve energy savings. During times of high daylight contribution to a space, controlled artificial lighting will be gradually dimmed to a minimum dimmed level. During times of no or low daylight contribution, controlled artificial lighting will increase back up to its maximum level. The sensor can also be configured to switch lighting off completely in maintained high daylight conditions. Additional configurable parameters include high & low trim levels and fade rates.
All photocells provide the option of selecting the ambient light threshold (e.g., setpoint) from a range of preset values or running an auto-selection mode where the unit will determine the setpoint based on the measured amount of light it is controlling.
Line voltage sensors are self-contained units that directly power from and switch 120/277 VAC. In a fixture mount application, they typically control a single fixture.
Warehouse Storage Area
Features / Fixture Mount Sensors
Auto-Setpoint Selection Mode
On/Off Control and/or Daylight Harvesting (Dimming)
Adjustable High & Low Dimming Trim Level
Electronically Timed Switching Designed for LED Fixture Control
Snap-In Chase Nipple Makes Installation Quick
Integrated Bracket Drops Sensor Below Bottom of Fixture
4.00” Diameter x 3.00” H
(10.16 x 7.62 cm)
Daylight Harvesting to Low Trim
Daylight Harvesting to Off
Photocell Override (On/ Off)
MVOLT (120-277 VAC)
800W @ 120 VAC
1200W @ 277 VAC
CFL, Electronic/Magnetic Ballasts
0-10 VDC Ballasts or Drivers
Compliant with IEC 60929 Annex E.2
32°F to 122°F (0°C to 50°C) – Standard
-40° F/C (with -HE Option)
Indoor Use Only
Sensors can be used to meet
ASHRAE 90.1, IECC, & Title 24
energy code requirements
There are two types of photocell operation; ON/OFF PHOTOCELL CONTROL and DAYLIGHT HARVESTING CONTROL (see descriptions below).
ON/OFF PHOTOCELL CONTROL
Recommended for warehouses, garage bays, storage, etc wherefully switching lighting off/on will not be noticed .
Photocell will switch lights off if ambient light level surpasses threshold and back on if level drops.
To prevent cycling of lights back on after lighting is turned off, a “deadband” level equal to the measured level of light being controlled is continuously maintained in the unit. For lighting to turn off the ambient light level must be higher than the sum of the setpoint and the deadband.
DAYLIGHT HARVESTING CONTROL
- Recommended for spaces where it is important to not distract occupants.
- Unit will gradually dim lighting in order to maximize energy savings while maintaining desired overall lighting level.
- After dimming to low trim level, unit can optionally be enabled to turn off lights completely.
Single Phase Wiring
2-Phase Wiring (208 VAC)
Daylight Harvesting to Off Wiring
- Dimming wires are present on models with -D option
Daylight Harvesting to Low Trim Wiring
Cap photocell load wire and connect fixture to constant hot feed.
EXAMPLE MODEL # SWX-550-D
|SWX–||Fixture Mount Photocell Sensor||550||Dimming / Daylight Harvesting (0-10V)||–D||Standard Environment||(Blank)|
|High Humidity Environment||–HE|
Ceiling Mount Photocell
This surface mount unit provides on/off photocell control, daylight harvesting (dimming), or a combination of both.
Wide View Sensors
With five contractor friendly mounting methods, locating a sensor in a corner has never been easier.
Mounting snaps and an optional low voltage wiring chamber make this power pack a breeze to install.